# Voltage induced by currents in power-line sagged conductors in nearby circuits of arbitrary configuration

Voltage induced by currents in power-line sagged conductors in nearby circuits of arbitrary... Abstract The study presents a calculation method of the voltage induced by power-line sagged conductor in an inductively coupled overhead circuit of arbitrary configuration isolated from ground. The method bases on the solution utilizing the magnetic vector potential for modeling 3D magnetic fields produced by sagging conductors of catenary electric power lines. It is assumed that the equation of the catenary exactly describes the line sag and the influence of currents induced in the earth on the distribution of power line magnetic field is neglected. The method derived is illustrated by exemplary calculations and the results obtained are partially compared with results computed by optional approach http://www.deepdyve.com/assets/images/DeepDyve-Logo-lg.png Archives of Electrical Engineering de Gruyter

# Voltage induced by currents in power-line sagged conductors in nearby circuits of arbitrary configuration

, Volume 64 (2) – Jun 1, 2015
10 pages

/lp/de-gruyter/voltage-induced-by-currents-in-power-line-sagged-conductors-in-nearby-d1qf8zL2p5
Publisher
de Gruyter
ISSN
2300-2506
eISSN
2300-2506
DOI
10.1515/aee-2015-0019
Publisher site
See Article on Publisher Site

### Abstract

Abstract The study presents a calculation method of the voltage induced by power-line sagged conductor in an inductively coupled overhead circuit of arbitrary configuration isolated from ground. The method bases on the solution utilizing the magnetic vector potential for modeling 3D magnetic fields produced by sagging conductors of catenary electric power lines. It is assumed that the equation of the catenary exactly describes the line sag and the influence of currents induced in the earth on the distribution of power line magnetic field is neglected. The method derived is illustrated by exemplary calculations and the results obtained are partially compared with results computed by optional approach

### Journal

Archives of Electrical Engineeringde Gruyter

Published: Jun 1, 2015